FireBoy - Xintex LPG Propane Gas Solenoid Valve
Fireboy-Xintex 1/4" Solenoid Valve
- Opens the flow of propane when powered
- Automatically closes with low or no current for added safety
- UL listed
- Power: 12 Volt DC
- Rated for 0 - 312 psi
- Fittings: 1/4" female NPT inlet, 1/4" male NPT outlet
- Includes 3/8" male flare x 1/4" female NPT brass fitting
- Orifice: 0.110"
SV-1 Electrical Solenoid Valve Installation:
A. LPG Installation The electrical solenoid valve should be mounted on the tank side of the LPG regulator, as close to the tank as practical. The tank itself should be mounted outside the cabin or crew quarters to avoid the possibility of gas accumulation due to a leak between the tank and solenoid valve.
B. CNG Installation Because of the higher tank pressure of CNG , the valve must be installed after the CNG regulator and as close to the regulator as possible. The tank itself should be mounted outside the cabin or crew quarters to avoid the possibility of gas accumulation due to a leak.
NOTE: After installation, all piping or hose joi nts must be checked for leaks with a soapy water solution. Never use a flame to test for leaks. NOTE: The solenoid provided is a normally closed solenoid and must have power applied to open
Item #: 400818